How much air is required for proper combustion? What if someone in the boiler room closes a window and cuts off adequate air supply to an individual boiler or the mechanical room in general? Is there a way to reduce the number or size of air intake louvers needed? Will my heating appliances pass a code inspection?
The ENERVEX Modulating Combustion Air Supply System takes the guesswork out of these types of challenges.
The MCAS system consists of an air supply fan, BEF, Box Ventilator and the EBC31, Modulating Fan Control. The EBC31 maintains a constant pressure in the mechanical room where the heating appliances are installed by modulating the speed of the supply fan. The MSC EDrive Motor Speed Control is also part of the system.
Each appliance is interlocked with the control. A call for heat activates the supply fan and releases the burner once the pre-set room pressure is established. The sequence is repeated every time a new heating appliance calls for heat. When an appliance shuts down, the fan will slow down while still maintaining the pressure setting. When the last appliance shuts down the supply fan will operate in post-purge mode for a preset time period.
The integrated proven pressure function will shut down the entire system in case of a power failure to the supply fan or the Motor Speed Controller or mechanical failure. During a following call for heat, the Operating Priority function will detect if one or more appliances can be operated safely and with proper air supply. If so, the appliance(s) will be able to operate without fan operation. After two (2) hours, fan operation is checked and if present, the control will go back to normal operation. Otherwise, it will continue to operate in Operating Priority mode. The self-check is repeated every two (2) hours infinitely. During a period without fan operation, the control is in alarm mode.
If the supply fan has been out of commission for seven (7) days, the Bearing Cycle Activation function will operate the fan at a low speed for a short time. This is automatically repeated every seven (7) days, if the fan has not been operating.
Any errors detected during operation are shown on the digital display screen.
Multi-use centrifugal exhaust fan designed for indoor and outdoor installation. Can be used for special exhaust or exhaust of lint-laden air. Also used to supply air.
A sophisticated multi-use draft and pressure controller with integrated webserver and remote access used with fans and dampers to monitor and maintain a constant pressure in commercial boiler and building applications.
A full featured, industrial-type motor controller programmed specifically to control and adjust the speed of ENERVEX fans and ventilators using Electronically Commutated (EC) Motors or Induction Motors.